This is completely off-topic, but seems worth a mention since it's a DIY crowd.
Two HVAC service/sales people came to my house, spent a combined 5 hours inspecting my frozen-up-and-not-blowing HVAC system, and then each recommended I get a completely new system after unsuccessful attempts to introduce new freon into my lines seemed to indicate everything was broken.
After desperate googling, I found there's a relay called a "contactor" that sits in the compressor unit, which can get stuck due to arcing or corroding or both, which can cause the compressor to never turn off (or on), and create a frozen-line situation which then leads to a ton of other performance issues.
So I flipped the breakers and gave this little mechanical relay's plunger a couple blasts of compressed air and WD-40, then a few whacks with the back end of my screwdriver, a few scrapes with the business end. Flipped the breakers back on and the system was working fine again after about 10 minutes of not-very-hard work.
So if your HVAC compressor quits running or won't quit running, try cleaning the contactor before calling the contractor.
Need help? Want to help? Discuss technical issues and share tips.
1 post • Page 1 of 1
Who is online
Users browsing this forum: No registered users and 3 guests